Electric gate valve
s have the longest history of use and are still used in various countries around the world, especially those below DN300mm, which still occupy a dominant position in various valves. The characteristic is that the pressure difference between the front and rear of the valve plate forces the valve plate to press on the valve seat on the right side of the outlet, with good sealing performance, and when the valve plate is fully opened, the pressure loss is small because the valve plate does not remain in the flow path. Used to cut off the medium in the pipeline. The disadvantage is that the operating torque is large, and the valve body and stem are easily damaged during operation, especially the large-caliber electric gate valve. The external size and weight are also large. The electric gate valve with DN1000 caliber is about 3200mm high and requires four people to operate it. Therefore, the electric gate valve is generally used in small diameters, that is, below DN500. The electric gate valve has a small flow resistance from fully open to middle opening, and when it is close to fully closed, the flow resistance increases sharply. In a larger range, the flow resistance changes less. When the valve is close to full closure, the flow change is large. Do not use it when the valve is close to closing. At this time, it is difficult to fine-tune the flow. If the valve opening is extremely small, the flow velocity at the opening is extremely fast, which will cause cavitation on the underside of the gate, accompanied by intense vibration and noise, and long-term throttling operation will often cause the metal of the valve body and gate to occur. Cavitation. If the operating condition of the electric gate valve is in the middle opening, the valve plate is supported by the guide rails on both sides, and it fits tightly when fully closed. In the middle position, the gap between the valve plate and the guide rail is large and vibration occurs. Therefore, even in areas where the incidence of cavitation is low, if the valve is throttled for a long time, the guide rail will be deformed, worn or damaged, and because the valve seat is not in full contact, and the surface pressure of the contact part is very high, it will often produce Biting or adhesion, therefore, it is not suitable for flow control. Also note that when the electric gate valve has a small opening, the flow changes greatly. If the electric valve is opened and closed in an emergency, it will cause a sharp rise in pressure or generate negative pressure, especially water hammer when the valve is closed.
Owing to its industrial valve
s china and industrial valves china benefits, has become a buzzword in the industrial valves china market.
If you want to know more about finding the proper for industrial valves china
solutions, visit Sino Global Industrial Valves.
Advanced technology and manufacturing equipment has enhanced the core quality of Contact Us.